ZoomLock vs Brazed Fittings.
Which piping joint method is best for your project? There are several things to consider.
What materials are the structure constructed of, and what is the occupancy of the building? If it is a wood structure then creates a greater risk of using a flame when brazing piping joints. If the occupancy is a senior facility or some other occupancy type that would create additional risk due to the occupant’s non-ambulatory ability or employees sensitivity to the byproducts of the brazing process.
Once you have considered the risk analysis based on occupancy and material structure type, then you can look at a cost analysis. The material for ZoomLock™ or other mechanical piping joints cost considerably more than the standard wrot copper brazed fitting.
ZoomLock™ is to be used only on copper to copper applications using either hard or soft copper. ZoomLock™ is a trademark of Parker Hannifin Corporation, the Sporlan Division. The technology is owned by RLS (a Berkshire Hathaway Company) and is licensed to Parker Hannifin.
HVAC Commercial vs Residential
The advantage may lean more towards the HVAC commercial and Industrial markets than that of residential. The HVAC commercial application provides more opportunities due to longer lengths of piping and the need for more fittings. With residential you might have 6 connections, two at the condenser, and two at the evaporator and another two if you’re installing a drier or site glass. There are additional advantages to using ZoomLock™ in both market sectors as discussed later.
Pressure Rating of ZoomLock™ Fittings
Are you concerned that the fittings won’t standup to the increased pressures in a R410A system as compared to R22?
- Rated at 700 psi / 48 bar
- Minimum burst pressure of 2,100 psi / 145 bar
- Maximum burst pressure of 3,000 psi / 207 bar
There is concern over the durability of the internal O-ring of the ZoomLock™ fitting. How many years will it last? Will it leak? What happens in a fire? Can you braze a failed ZoomLock™ fitting?
- Temperature Rated -40 F to +300 F (-40 C to +149 C)
- Material HNBR – Hydrogenated Nitrile Butadiene Rubber
- Life of O-Ring – 30 years when used with the temperature & pressure ratings according to ZoomLock
- Don’t braze a fitting as this could cause the O-Ring to contaminate the system.
Just remember they use O-rings on the space shuttle and just about any type of military aircraft. If its good enough for NASA, may be its good enough for a refrigerant fitting.
Smoke, Smell, Fire Watch & Burn Permits
When brazing in an enclosed area within a building you will need to be aware of the location of smoke detectors or deactivate them in some way to avoid setting off the annoying little screamers. In some commercial facilities the smell caused by brazing could raise concerns amongst the occupants, such as those with chemical sensitivities or within a senior living facility.
Also, if you have a flammable storage area or other rooms that contain materials easily ignited, a flameless application will work best. With ZoomLock™ you won’t get any customer or employee complaints about smell. Depending on the facility and the jurisdiction you may also be required to have a fire watch, which adds additional cost to your project.
If you have a concern over whether or not theses fittings are accepted in your jurisdiction, then you should know that there is a good chance they are. The following certifications and agency approvals are usually adopted into most local codes in some form.
- 2015 IMC (International Mechanical Code)
- 2015 UMC (Uniform Mechanical Code)
- 2015 IRC (International Residential Code)
- ASHRAE 15
- UL 207, SA#33958, SDTW(7)(Except where noted)
- CRN (Approved for couplings & 90 Degree Elbows)
We’re always concerned about the warranty, which is a good indication of the manufactures belief in their own manufacturing process and fitting. Currently ZoomLock™ offers a 5-year warranty with a full page of terms and conditions, read page 28 of their K-1 Catalog dated June 2017.
What happens in an earthquake or when equipment vibrates? Can the fitting hold under such conditions? See UL109
Here is ZoomLocks response to the use of their fitting in a transportation application where the vibration level is high. “ZoomLock™ has gone through extensive vibration testing and results are actually better than that of a braze joint. Please review the vibration testing procedure and conclusion for more information.”
Available Sizes of ZoomLock™ Fittings
Available ZoomLock™ Fittings
- 90 Degree Long Radius Elbows
- SAE Flare
- Y-Joints (Coming Soon)
- 45 Degree Elbows (Coming Soon)
- P-Traps (Coming Soon)
- Reducing Bushings (Coming Soon)
According to ZoomLock™ the tool has a red LED on the back of the tool that will blink for 20 seconds after a crimp. When this occurs, take the tool back to an authorized dealer to have the tool analyzed. They will be able to verify if the tool needs to be sent in for service.
- Life of Jaws – 10,000 to 12,000 Crimps
- Battery – 100 to 150 Crimps* (15 Minute Charging Time)(2.0 Ah)
- Warranty – 24 Months from date of purchase (Verify with supplier)
- Klauke 19 kN required for 1-3/8” size fittings
*According to ZoomLock™ you can get 100 to 150 Crimps depending on the sizes used. The system comes with two batteries, so this extends your capabilities up to between 200 to 300 crimps. Make sure you go to the jobsite with your batteries fully charged. The equivalent with brazing is that you will need to replenish your gases when depleted.
Crimp Tool Manufactures & Models
- Klauke 15 kN MAP2LCER (J Series Jaw)
- Klauke 19 kN MAP2L19 (KJ Series Jaw)
- Ridgid RP 100-B (RJ Series Jaw)
- Ridgid RP 200-B (RJ Series Jaw)
- Ridgid RP 210-B (RJ Series Jaw)
What do you do if your HVAC unit ships with flared ends at the connection points? ZoomLock suggest that if you have at least two inches and room to fit the crimp tool, then cut off the flare and use their fitting.
ZoomLock™ Cost Analysis
ZoomLock claims on their site that the fitting only requires 10 seconds and can save up to 60% of your labor cost. See our post about ZoomLock Cost Analysis (Brazed versus Zoomlock).
You Can’t Teach an Old Dog New Tricks
For those of you who are a little older and are stuck in your ways, changing to a new way of doing things is usually met with resistance. Maybe you still have VHS tapes or don’t market your company on the internet. Using ZoomLock™ is changing the way the industry installs refrigerant piping, it’s just a matter of time before it becomes more prevalent. Also checkout the SmartLock Fitting as it claims a 90% savings over brazed fittings.
Manufactures will keep investing in ways to reduce labor and make installations simpler in hopes of earning your money for doing so. When installed correctly you should have a satisfied customer, at least for 30 years, and by then there will be some other labor saving fitting or system that you can sell to replace the old one.
Leave us a comment below about your experience with ZoomLock or why you haven’t tried it yet. ZoomLock is a trademark of Parker Hannifin Corp.
Sign Up For Our Newsletter to stay informed on the latest in VRF / VRV